|Minimum Order Quantity
|Karmyogi Cooling Industries
|5 to 100 Tons
|Air Flow Range
|30 mm to 125 mm
Our AHU comes with CFM ranging from 800 CFM to 40000 CFM, Static Pressure ranging from 40 mm WC to 150 mm WC, Imported Fan Selection – SISW, DIDW, EC & Plug Type. The compact design is maintenance friendly, vibration free & noiseless in performance. Filters & Coil Selection is done in a manner to attain efficient results. Mixing Chambers, Humidifiers & Specialized Aero foil / Motorized Dampers available on specific demand.
v Double Skin AHU with 40 to 50 mm Fiber Glass Insulation or 25 mm Foam Insulation with 0.9 to 1 mm G.I. outer & 0.8 mm inner skin.
v Single Skin AHU with 25 mm Fiber Glass Insulation or 15 mm thick foam insulation with 0.7 to 0.8 mm G.I. outer & 0.5 mm inner skin
v Ceiling Suspended Ductable Units
v Fresh Air & Exhaust Air Ventilation Units (As Required)
v Treated Fresh Air Unit
Ø In Ahu, The Assembly Includes A Frame Composed Of A Specially Shaped Section Of Extra-Thick G.I. Sheet With High Bending Strength, Due To The Pleats In Frame.
Ø The Inner Rack Is Manufactured Of Plain G.I. Sheet, Whereas The Exterior Rack Of The Same Material Has A Backed On Pre Enamel Coated.
Ø The Space Is Crated By The Connection Of The Two Racks Is Filled With An Injected CFC Polyurethane Foam Insulation having 38-40 kg/cum To Ensure Excellent Thermal And Sound Insulation That Prevents Heat Transfer, Noise Transmission And Potential Condensation.
Ø The Frame Sections Are Joined By Angle Cleats Manufactured Of Die-Cast Aluminum.
Ø Drain Pan is made of S.S. 304 construction to avoid rusting.
We Manufactured Of Pre Filters & Fine Filters In Aluminum, G.I. & S.S. Construction As Per Standards.
v Pre-Filter (Filtration Range- 10µ)
v Fine Filter (Filtration Range- 3µ to 5µ)
v Return Air Riser Filter (Filtration Range- 10µ to 20µ)
v HEPA Filter (Filtration Range up to 0.3µ)
Ø This section is composed of a double inlet cone centrifugal fan with an anchor bedplate, drive and electric motor or plug-fan.
Ø Forward-Facing Impeller Blades and are used in facilities designed to run with low-pressure air flow. These fans are identified with the AT and ADH codes.
Ø Backward Curved Blades and is designated RDH, is used for facilities with medium- or high-pressure air flow.
Ø The Motor-Fan Drive Is Composed Of Pulleys And V-Belts.